APS was involved with this fast track, large (over 50,000 sq. ft), data room buildout from the ground up. A unistrut grid was built underneath the raised floor in order to support the massive amount of equipment (relay rack, batteries, cable, ladder rack, and aux bar) that was installed above. Each rack was supported with (4) 5/8″ all threads per rack.
From a power equipment standpoint, we installed (1) FBO 4848 DC power plant with (1) Supplemental Bay, (6) 200A rectifiers, and a building ground bus. Included was connection of (2) strings of 48VDC batteries along with IEEE disconnects, (1) temperature probe per battery string, battery disconnect alarming, and the 750MCM cabling from batteries to the power plant, along with commissioning.
APS installed (71) FBO 2 post racks, (26) FBO 4 post racks, FBO fiber bay, (6) FBO BDCBB’s, (36) FBO 60A FAP’s, and (28) FBO 200A FAP’s. We installed low/high aux bar, low/high ladder rack, ground hangars, and 4″ fiber tray with 4″ drops to each bay. We installed customer furnished racks, spacers, and grounding of each rack with #6 wire to a #2 aisle ground. We installed customer provided BDCBB’s and (2) 600A loads to each BDCBB (single 500MCM wire per load). Project also included running loads from the BDCBB’s to the customer provided FAP’s using wire and lugs provided by customer. All wires were labeled.